646.757.4500 • 800.605.1500
Federal Pacific Electric (FPE)
Stab-Lok Circuit Breaker Panels
Insight Only An Engineer Offers
Home, Building, Condo, and Co-op Inspections
in Manhattan, Queens, Brooklyn, Bronx,
Staten Island, Nassau, Suffolk, Rockland,
Putnam, and Westchester
646.757.4500 • 800.605.1500
An Engineer's inspection, a pre-purchase inspection, and a termite inspection. You receive four reports: an onsite verbal report, an onsite written report, an emailed written report, and a termite report. Call 800.605.1500 or 646.757.4500 if you have questions. We are happy to help you.
Click on the blue boxes to navigate this website.
Federal Pacific Electric Stab-Lok circuit breakers received a lot of bad press because of their failure to meet certain Underwriter's Laboratories (UL) test requirements. The Consumer Product Safety Commission (CPSC) investigated the claims, and determined that it had insufficient data to make a determination. Federal Pacific Electric (which is now out of business) acknowledged that the circuit breakers do not meet all of the UL standards, but stated that the circuit breakers would only fail under conditions considered abusive.
There are a lot of websites that talk about serious hazards associated with Federal Pacific Electric Stab-Lok circuit breaker panels. Many are alarmists who exaggerate the CPSC's findings. Some of the websites appear to be electricians trying to create work, while others are home inspectors who exaggerate the claims.
There has been renewed interest in the risks of Federal Pacific Electric Stab-Lok circuit breaker panels because of recent news reports of fires. What is not included in the news stories is a comparison with electrical fires caused by non-Federal Pacific Electric circuit breakers. Electrical fires happen every day, and they are not all caused by Federal Pacific Electric Stab-Lok circuit breakers. It is the history of false test reports that condemns Federal Pacific Electric Stab-Lok circuit breakers.
As Licensed Engineers, it is our responsibility to help protect the public. In addition, a Licensed Engineer has the responsibility not to be an alarmist or overstate a hazard. Given this need for balance, it is our recommendation that an old Federal Pacific Electric Stab-Lok circuit breaker panel be treated as old electric wiring.
Old circuit breaker panels in homes, buildings, condos, and co-ops are outdated by today's standards. Circuit breakers can deteriorate over time. The fact that the panel was manufactured by a Federal Pacific Electric, along with other aspects of the electrical system, should be taken into account when deciding if a circuit breaker panel needs to be replaced.
Old circuit breaker panels are
outdated by today's standards
Unfortunately, some home inspectors have decided that all Federal Pacific Electric Stab-Lok circuit breaker panel needs to be replaced, and have ignored other old circuit breaker panels. These home inspectors accuse the now-defunct manufacturer of these panels of wrongdoing, and recommend panel replacement based only on that accusation.
Many home inspectors fail to look at the age of the circuit breaker panel as the cause of recent fires attributed to Federal Pacific Electric Stab-Lok circuit breaker panels. It is vital that the age and not just the manufacturer of the circuit breaker panels be assessed in determining the risk. Be careful of any home inspector who only looks only at the manufacturer when assessing a circuit breaker panel. A hazardous condition could be missed.
Only a Licensed Electrician should open a circuit breaker or fuse panel because of the risks. An Inspector or anyone else who is not a Licensed Electrician should never open a circuit breaker or fuse panel.
A Licensed Electrician can correct hazardous conditions created by opening electrical panels. Someone who is not a Licensed Electrician lacks the experience to deal with hazardous conditions. If a problem develops because of opening the panel (for example, a circuit breaker becomes loose), the Inspector is not in a position to resolve the problem. A responsible home inspector will not open electrical panels.
Most communities require electricians to be licensed, and prohibit anyone other than a Licensed Electrician from performing electrical work. (Exceptions are made for homeowners wiring their own home.)
An experienced Engineer can determine the condition of the wiring by visual examination. The question is why do some home inspectors insist on opening the circuit breaker panel when it could create a hazard. Can't these home inspectors see the risks and hazards on the outside? Are these home inspectors missing wiring problems because of their narrow focus?
During the inspection, the Licensed Engineer examines, analyzes, and/or reports on (as appropriate based on the building):
Contact Heimer Engineering 24/7
Heimer Engineering is happy to help you. Staff members are available to answer your questions from Monday through Friday from 9:15 AM to 5:00 PM. Messages are checked Sunday evening through Thursday evening. Inspections are performed seven days a week.
To set up an appointment for a pre-purchase inspection, or to find out about Engineering services or expert court testimony, click below for a contact form, send us an email, send a text to 888.769.6910, call 646.757.4500, or call 800.605.1500. If no staff member is in the office, leave a message. Remember to ask about a web discount.
Heimer Engineering serves the Metro New York area, including New York City (Manhattan, Queens, Brooklyn, Bronx, Staten Island), Long Island (Nassau County, Suffolk County, and Upstate New York (Rockland County, Putnam County, and Westchester County).
Heimer Engineering respects your privacy. Some inspection firms share information with insurance, landscaping, home maintenance, moving, cable, mortgage, and other companies. You will not receive phone calls or solicitation emails from third parties as a result of providing personal information.
In the event of a life-threatening emergency call 911. Emergency situations need to be handled by first-responders who can evacuate buildings, shut utilities off, and take other steps necessary to preserve life.
In addition to the webpage discount, discounts are available for referrals (attorney, real estate broker, mortgage broker, co-worker, friend) first time buyers, senior citizens, military (army, navy, air force, marines, coast guard), first responders (police, ambulance, fire), municipal employees, security personnel, and union members.
Translate This Webpage
|Using Google Translate, you can view this webpage in the language of your choice.|
Heimer Engineering performs home inspections, building inspections, condominium inspections, and co-op inspections in the State of New York. We do not perform inspections or recommend Inspectors or Engineers outside of the State of New York. We provide Licensed Professional Engineer consultation services including hurricane and storm damage and damage from adjoining construction. Expert witness services are provided regarding playground injuries, parking lot, walkway, and stairway slip, trip, and fall.
The website was designed by Harold Krongelb. Post design review was performed by Matthew John Rapisarda. Sitemaps and indexing information can be found at Page Sitemap, Image Sitemap, and Video Sitemap. Heimer Engineering's domains include www.heimer.com, www.expert-witness-ny.com, www.home-inspection-ny.com, www.professional-engineer.com, and www.home-inspection-engineer.com. Heimer Engineering posts updates on Facebook.
This page was published on .
This page was loaded:
(C) 1997-2017 Heimer Engineering PC. All rights reserved. Used under license by Heimer Engineering PC.
2171 Jericho Turnpike, Suite 230
Commack, New York, USA 11725-2947
• New York Metro Area: 800.605.1500, 646.757.4500
• Bronx, New York: 718.547.2000
• Brooklyn, New York: 718.237.7777
• Manhattan, New York: 212.563.4777
• Long Island, New York: 631.549.2500
• Nassau County, New York: 516.487.2100
• Putnam County, New York: 845.638.4900
• Queens, New York: 718.544.3000
• Staten Island, New York: 718.227.5000
• Suffolk County, New York: 631.858.5500, 631.288.3900
• Westchester County, New York: 914.576.6100
• Fax: 631.858.5599, 646.795.4571
• Text: 888.769.6910
• Coordinates: 40.8439215, -73.2871259
• URL: www.heimer.com
• Email: Info@heimer.com
International Standard of Industrial Classification of All Economic Activities (ISIC) Revision 4 Classification: 71
North American Industry Classification System (SAISC) Classification: 541330, 541350